Cabling / Wiring Issue
I've been trying to figure out how to create the following scenario:
UPS-A receive connection (power) from PowerCompany-A and B.
UPS-B receive connection (power) from PowerCompany-B and A.
Both UPS have one output each to PDU-A and PDU-B.
I've been struggling to know how to connect two devices on a "Y" connection (two inputs that goes to one output) using the Pro version. I've looked at the demo (object "USV HQ") but I couldn't figure out how.
Thanks for your request. There is an easy way to connect one input with two or more outputs: Just create one input (with no connected output) and then two outputs connected to the input. You will get a similar result as in the online demo for i-doit pro.
The other way (two inputs connected to one output) is currently not possible with i-doit pro. Can you give us a simple drawing which scenario in real life you would like to document? Maybe there is a workaround.